Trane Co. in cooperation with the CPSC announced a voluntary recall of about 10,580 PTEE and PTHE Series Packaged Terminal Air Conditioners (PTACs) manufactured by Qingdao Haier Air Conditioner, of Qingdao, China.
The heating element on these commercially installed units can become displaced and, if it contacts metal, could short circuit. If the electric heater on one of those units short-circuits, wiring problems on 265 V models could allow the unit to remain energized while the unit’s fan is turned off, causing it to overheat and smoke. Individuals installing units observed smoking and smelled a burning odor in three units during installation testing procedures. No injuries have been reported.
The recall includes 208, 230 and 265 V models of the Trane PTEE and PTHE Series
Packaged Terminal Air Conditioners (PTACs). They were manufactured from about March 2006 through July 2006. The date code is F06C through F06G, and is written on the unit’s Manufacturer’s Data Plate located behind the molded plastic cover above the power connection. The units have the following model numbers, also written on the Manufacturer’s Data Plate: PTEE0701UAA, PTEE1501UAA, PTHE0902UAA, PTEE0702UAA, PTEE1502UAA, PTHE1201UAA, PTEE0901UAA, PTHE0701UAA PTHE1202UAA, PTEE0902UAA, PTHE0702UAA, PTHE1501UAA, PTEE1201UAA PTHE0901UAA, PTHE1502UAA, and PTEE1202UAA.
Trane distributors sold the recalled units to commercial customers for use in locations such as hotels and office buildings from May 2006 to July 2006. The power connectors are being rewired or replaced, and the heaters will be visually inspected and replaced as necessary in the 265 V models. Although there have been no incidents with the 208-Vand 230-V models, Trane is still inspecting these units as a precaution. Trane has contacted the affected customers directly.
to Daily News